Complete pump end and motor set. Complete Instructions. Tuhorse Control Panel sold separately.
If you do not purchase a Tuhorse Control Panel for this pump, below is the mimimum requirement for operating and protecting the pump.
Minimum requirement for operating the motor is a non-fused 3-phase power switch and a 3-phase overload protector / Circuit breaker. The protector / breaker must be the type of those that shut off all 3-phase when one or more phase is overloaded. Do NOT use a fused switch that could burn out one of the phase. Do NOT use 3 x 1-Phase breakers, You must use a real 3-phase breaker that do not cause missing phase problem.